What are the inspection contents of the secondary water supply monitoring system
The secondary water supply on-line monitoring system is relatively common in various high-rise communities. Since the municipal water supply is generally only below the sixth floor, most of the upper floors use secondary water supply. In order to ensure the water quality of the secondary water supply, generally It is necessary to install the secondary water supply online monitoring system for water quality analysis, and in order to ensure the long-term operation of the equipment, regular inspections are required. Let me tell you about the inspection contents of the secondary water supply monitoring system. Inspection content of the secondary water supply monitoring system 1. The duty personnel need to check the operation status of the secondary water supply system and the variable frequency pump every time (judging whether the sound of the equipment is normal, and checking whether the pressure reading of the equipment is within the normal range). The method is to judge whether the frequency conversion pump has a fever phenomenon. If the overheating is generally caused by excessive water consumption, it needs to be cooled in time. When the frequency conversion pump fails and heats up, it needs to be stopped in time and recorded. 2. Check the operation of the water supply pump. It is necessary to check whether it can operate normally. If there is an abnormality, it must be resolved in time and recorded. 3. Open the door of the power distribution cabinet of the equipment frequency conversion pump to check, check whether the line is burnt, whether the air switch device is in the normal position (if there is any abnormality, it needs to be solved in time), check whether the indicator light on the panel of the power distribution cabinet is normal, If there are stains during the inspection process, the impurities left by the project must be dealt with in time. 4. Check whether there is water leakage, damage, corrosion, etc. in the equipment inlet and outlet pipes, valves and other devices. 5. The operation of the secondary water supply online detector system needs to be regularly and accurately recorded every day to ensure that the equipment can operate normally. 6. The daily cleanliness of the underground pump room should be maintained. 7. Inspection results should be complete and clearly recorded. The above is the introduction of the inspection content of the secondary water supply monitoring system. In order to ensure the normal operation of the equipment, it is necessary to regularly check whether the installed equipment can operate normally.